(A) Where a subsurface seepage field is installed as a component part of a private sewage disposal system, the seepage area provided shall be in accordance with the Private Sewage Disposal Licensing Act and Code. A minimum of three hundred (300) square feet of seepage area shall be provided.
(B) An effluent reduction system, equal to one hundred (100) square feet of absorption area per bedroom, shall be installed after a surface discharging unit (excepting lagoons and sandfilters) if the effluent from the system:
will be discharged in a high density residential area and, the effluent discharge point is within fifty (50) feet of the property line or building setback line, or ten (10) feet of the right-of-way, whichever provides for the greatest distance, and/or
the discharge is to a body of water (state, county or township roadside ditch, waterway, creek, lake). This shall not apply to a discharge to a pond or lake that is privately owned by the person whom the system is serving.